Commission Regulation (EU) No 547/2012
of 25 June 2012
implementing Directive 2009/125/EC of the European Parliament and of the Council with regard to ecodesign requirements for water pumps
(Text with EEA relevance)

THE EUROPEAN COMMISSION,
Having regard to the Treaty on the Functioning of the European Union,
Having regard to Directive 2009/125/EC of the European Parliament and of the Council of 21 October 2009 establishing a framework for the setting of ecodesign requirements for energy-related products, and in particular Article 15(1) thereof,
OJ L 285, 31.10.2009, p. 10.
After consulting the Ecodesign Consultation Forum,
Whereas:
(1) Under Directive 2009/125/EC, ecodesign requirements are to be set by the Commission for energy-related products representing significant volumes of sales and trade, having a significant environmental impact and presenting significant potential for improvement in terms of their environmental impact without entailing excessive costs.
(2) Article 16(2) of Directive 2009/125/EC provides that, in accordance with the procedure referred to in Article 19(3) and the criteria set out in Article 15(2), and after consulting the Consultation Forum, the Commission shall, as appropriate, introduce implementing measures for products used in electric motor systems, such as water pumps.
(3) Water pumps forming parts of electric motor systems are essential in various pumping processes. There is a total cost-effective potential for improving the energy efficiency of these pumping systems by approximately 20 % to 30 %. Even though the main savings can be achieved by motors, one of the factors contributing to such improvements is the use of energy-efficient pumps. Consequently, water pumps are a priority product for which ecodesign requirements should be established.
(4) Electric motor systems include a number of energy-related products, such as motors, drives, pumps or fans. Water pumps are one of these products. Minimum requirements are established for motors in a separate measure, Commission Regulation (EC) No 640/2009. Consequently, the present Regulation only sets minimum requirements for the hydraulic performance of water pumps without the motor.
OJ L 191, 23.7.2009, p. 26.
(5) Many pumps are integrated in other products without being separately placed on the market. To achieve the full cost-effective energy-saving potential, water pumps integrated in other products should also be subject to the provisions of this Regulation.
(6) The Commission has carried out a preparatory study to analyse the technical, environmental and economic aspects of water pumps. The study has been developed together with stakeholders and interested parties from the Union and third countries, and the results have been made publicly available.
(7) The preparatory study shows that water pumps are placed on the European Union market in large quantities. Their energy consumption in the use phase is the most significant environmental aspect of all life-cycle phases, with their annual electricity consumption amounting to 109 TWh in 2005, corresponding to 50 Mt in CO2 emissions. In the absence of measures to limit this consumption, it is predicted that energy consumption will increase to 136 TWh in 2020. It has been concluded that use-phase electricity consumption can be improved significantly.
(8) The preparatory study shows that electricity consumption in the use phase is the only significant ecodesign parameter related to product design as referred to in Annex I, Part 1, to Directive 2009/125/EC.
(9) Improvements in electricity consumption in the use phase of water pumps should be achieved by applying existing non-proprietary cost-effective technologies that can reduce the total combined costs of purchase and operation.
(10) Ecodesign requirements should harmonise power consumption requirements for water pumps throughout the European Union, thus contributing to the functioning of the internal market and to the improvement of the environmental performance of these products.
(11) An appropriate timeframe should be provided for manufacturers to redesign products. The timeframe should be such as to avoid negative impacts on the functionalities of water pumps and to take into account cost impacts for manufacturers, in particular small and medium-sized enterprises, while ensuring timely achievement of the objectives of this Regulation.
(12) Power consumption should be determined using reliable, accurate and reproducible measurement methods, which take into account the recognised state-of-the-art including, where available, harmonised standards adopted by the European standardisation bodies, as listed in Annex I to Directive 98/34/EC of the European Parliament and of the Council of 22 June 1998 laying down a procedure for the provision of information in the field of technical standards and regulations and of rules on Information Society services.
OJ L 204, 21.7.1998, p. 37.
(13) This Regulation should increase the market penetration of technologies that improve the life-cycle environmental impact of water pumps, leading to estimated energy savings of 3,3 TWh by 2020, compared to the situation where no measures are taken.
(14) In accordance with Article 8(2) of Directive 2009/125/EC, this Regulation should specify the applicable conformity assessment procedures.
(15) In order to facilitate compliance checks, manufacturers should provide information in the technical documentation referred to in Annexes IV and V to Directive 2009/125/EC.
(16) In order to further limit the environmental impact of water pumps, manufacturers should provide relevant information on disassembly, recycling or disposal at end-of-life.
(17) Benchmarks for currently available technologies with high energy efficiency should be identified. This will help to ensure the wide availability and easy accessibility of information, in particular for small and medium-sized enterprises, which will further facilitate the integration of the best available technologies for reducing energy consumption.
(18) The measures provided for in this Regulation are in accordance with the opinion of the Committee established by Article 19(1) of Directive 2009/125/EC,
HAS ADOPTED THIS REGULATION:

Article 1 Subject matter and scope
1. This Regulation establishes ecodesign requirements for the placing on the market of rotodynamic water pumps for pumping clean water, including where integrated in other products.
2. This Regulation shall not apply to:
(a) water pumps designed specifically for pumping clean water at temperatures below – 10 °C or above 120 °C, except with regard to the information requirements of Annex II, points 2(11) to 2(13);
(b) water pumps designed only for fire-fighting applications;
(c) displacement water pumps;
(d) self-priming water pumps.

Article 2 Definitions
The definitions set out in the Ecodesign for Energy-Related Products Regulations 2010 apply; and for any term that is not defined in those Regulations, the definitions set out in Directive 2009/125/EC of the European Parliament and of the Council of 21 October 2009 establishing a framework for the setting of ecodesign requirements for energy-related products, as it had effect immediately before IP completion day, apply. The following definitions also apply—
(1) ‘water pump’ is the hydraulic part of a device that moves clean water by physical or mechanical action and is of one of the following designs:
End suction own bearing (ESOB),
End suction close coupled (ESCC),
End suction close coupled inline (ESCCi),
Vertical multistage (MS-V),
Submersible multistage (MSS);
(2) ‘End suction water pump’ means a glanded single stage end suction rotodynamic water pump designed for pressures up to 16 bar, with a specific speed ns between 6 and 80 rpm, a minimum rated flow of 6 m3/h (1,667·10–3 m3/s), a maximum shaft power of 150 kW, a maximum head of 90 m at nominal speed of 1 450 rpm and a maximum head of 140 m at nominal speed of 2 900 rpm;
(3) ‘Rated flow’ means the head and flow that the manufacturer will guarantee under normal operating conditions;
(4) ‘Glanded’ means sealed shaft connection between the impeller in the pump body and the motor. The driving motor component remains dry;
(5) ‘End suction own bearing water pump’ (ESOB) is an end suction water pump with own bearings;
(6) ‘End suction close coupled water pump’ (ESCC) is an end suction water pump of which the motor shaft is extended to become also the pump shaft;
(7) ‘End suction close coupled inline water pump’ (ESCCi) means a water pump of which the water inlet of the pump is on the same axis as the water outlet of the pump;
(8) ‘Vertical multistage water pump’ (MS-V) means a glanded multi stage (i > 1) rotodynamic water pump in which the impellers are assembled on a vertical rotating shaft, which is designed for pressures up to 25 bar, with a nominal speed of 2 900 rpm and a maximum flow of 100 m3/h (27,78·10–3 m3/s);
(9) ‘Submersible multistage water pump’ (MSS) means a multi stage (i > 1) rotodynamic water pump with a nominal outer diameter of 4″ (10,16 cm) or 6″ (15,24 cm) designed to be operated in a borehole at nominal speed of 2 900 rpm, at operating temperatures within a range of 0 °C and 90 °C;
(10) ‘rotodynamic water pump’ means a water pump that moves clean water by means of hydrodynamic forces;
(11) ‘displacement water pump’ means a water pump that moves clean water by enclosing a volume of clean water and forcing this volume to the outlet of the pump;
(12) ‘self-priming water pump’ means a water pump that moves clean water and which can start and/or operate also when only partly filled with water;
(13) ‘clean water’ means water with a maximum non-absorbent free solid content of 0,25 kg/m3, and with a maximum dissolved solid content of 50 kg/m3, provided that the total gas content of the water does not exceed the saturation volume. Any additives that are needed to avoid water freezing down to – 10 °C shall not be taken into account.
The definitions for the purpose of Annexes II to V are set out in Annex I.
Words in Art. 2 substituted (31.12.2020) by The Ecodesign for Energy-Related Products and Energy Information (Amendment) (EU Exit) Regulations 2019 (S.I. 2019/539), reg. 1(3), Sch. 2 para. 14(2) (as amended by S.I. 2020/1528, regs. 1(2), 4); 2020 c. 1, Sch. 5 para. 1(1)

Article 3 Ecodesign requirements
The minimum efficiency requirements as well as information requirements for rotodynamic water pumps are set out in Annex II.
Ecodesign requirements shall apply in accordance with the following timetable:
(1) from 1 January 2013, water pumps shall have a minimum efficiency as defined in Annex II, point 1(a);
(2) from 1 January 2015, water pumps shall have a minimum efficiency as defined in Annex II, point 1(b);
(3) from 1 January 2013, the information on water pumps shall comply with the requirements set out in Annex II, point 2.
Compliance with ecodesign requirements shall be measured and calculated in accordance with requirements set out in Annex III.
No ecodesign requirement is necessary regarding any other ecodesign parameter referred to in Annex I, Part 1, of Directive 2009/125/EC.

Article 4 Conformity assessment
For the purposes of regulation 4(2)(a) of the Ecodesign for Energy-Related Products Regulations 2010, the procedure for assessing whether an energy-related product complies with this implementing measure is the internal design control system set out in Part 1 of Schedule 1A to the Ecodesign for Energy-Related Products Regulations 2010 or the management system for assessing conformity set out in Part 2 of Schedule 1A to those Regulations.
Art. 4 substituted (31.12.2020) by The Ecodesign for Energy-Related Products and Energy Information (Amendment) (EU Exit) Regulations 2019 (S.I. 2019/539), reg. 1(3), Sch. 2 para. 14(3); 2020 c. 1, Sch. 5 para. 1(1)

Article 5 Verification procedure for market surveillance purposes
When performing market surveillance checks to assess compliance with the requirements set out in Annex 2, the authorities of Great Britain must apply the verification procedure described in Annex 4.
Art. 5 substituted (31.12.2020) by The Ecodesign for Energy-Related Products and Energy Information (Amendment) (EU Exit) Regulations 2019 (S.I. 2019/539), reg. 1(3), Sch. 2 para. 14(4) (as amended by S.I. 2020/1528, regs. 1(2), 6(3)(4)(b)(xiii)); 2020 c. 1, Sch. 5 para. 1(1)

Article 6 Indicative benchmarks
The indicative benchmarks for the best-performing water pumps available on the market at the time of entry into force of this Regulation are set out in Annex V.

Article 7 Revision
. . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .
Art. 7 omitted (31.12.2020) by virtue of The Ecodesign for Energy-Related Products and Energy Information (Amendment) (EU Exit) Regulations 2019 (S.I. 2019/539), reg. 1(3), Sch. 2 para. 14(5); 2020 c. 1, Sch. 5 para. 1(1)

Article 8 Entry into force
This Regulation shall enter into force on the twentieth day following that of its publication in the Official Journal of the European Union.
...
Words in Signature omitted (31.12.2020) by virtue of The Ecodesign for Energy-Related Products and Energy Information (Amendment) (EU Exit) Regulations 2019 (S.I. 2019/539), reg. 1(3), Sch. 2 para. 14(6); 2020 c. 1, Sch. 5 para. 1(1)

ANNEX I Definitions applicable for the purposes of Annexes II to V
For the purpose of Annexes II to V, the following definitions apply:
(1) ‘Impeller’ means the rotating component of a rotodynamic pump which transfers energy to the water;
(2) ‘Full impeller’ means the impeller with the maximum diameter for which performance characteristics are given for a pump size in the catalogues of a water pump manufacturer;
(3) ‘Specific speed’ (ns) means a dimensional value characterising the shape of the water pump impeller by head, flow and speed (n):
ns= n ×QBEP1∕iHBEP34
[min–1]
Where
‘Head’ (H) means the increase in the hydraulic energy of water in meters [m], produced by the water pump at the specified point of operation,
‘Rotational speed’ (n) means the number of revolutions per minute [rpm] of the shaft,
‘Flow’ (Q) means the volume flow rate [m3/s] of water through the water pump,
‘Stage’ (i) means the number of series impellers in the water pump,
‘Best efficiency point’ (BEP) means the operating point of the water pump at which it is at the maximum hydraulic pump efficiency measured with clean cold water,
(4) ‘Hydraulic pump efficiency’ (η) is the ratio between the mechanical power transferred to the liquid during its passage through the water pump and the mechanical input power transmitted to the pump at its shaft;
(5) ‘Clean cold water’ means clean water to be used for pump testing, with a maximum kinematic viscosity of 1,5 × 10–6 m2/s, a maximum density of 1 050 kg/m3 and a maximum temperature of 40 °C;
(6) ‘Part load’ (PL) means the operating point of the water pump at 75 % of the flow at BEP;
(7) ‘Over load’ (OL) means the operating point of the water pump at 110 % of the flow at BEP;
(8) ‘Minimum Efficiency Index’ (MEI) means the dimensionless scale unit for hydraulic pump efficiency at BEP, PL and OL;
(9) ‘C’ means a constant for each specific water pump type quantifying the differences in efficiency for different pump types.

ANNEX II Ecodesign requirements for water pumps

1. EFFICIENCY REQUIREMENTS

(a) From 1 January 2013, water pumps shall have a minimum efficiency:
at the best efficiency point (BEP) of at least (ηΒΕΡ) min requ, when measured according to Annex III, and calculated with the C-value for MEI = 0,1, according to Annex III,
a minimum efficiency at part load (PL) of at least (ηΡL) min requ when measured according to Annex III, and calculated with the C-value for MEI = 0,1, according to Annex III,
a minimum efficiency at over load (OL) of at least (ηΟL) min requ when measured according to Annex III and calculated with the C-value for MEI = 0,1, according to Annex III.

(b) From 1 January 2015, water pumps shall have:
a minimum efficiency at the best efficiency point (BEP) of at least (ηΒΕΡ) min requ when measured according to Annex III and calculated with the C-value for MEI = 0,4, according to Annex III,
a minimum efficiency at part load (PL) of at least (ηΡL) min requ when measured according to Annex III and calculated with the C-value for MEI = 0,4, according to Annex III,
a minimum efficiency at over load (OL) of at least (ηΟL) min requ when measured according to Annex III and calculated with the C-value for MEI = 0,4, according to Annex III.

2. PRODUCT INFORMATION REQUIREMENTS
From 1 January 2013, the information on water pumps referred to in Article 1 set out in following points (1) to (15) shall be visibly displayed on:
(a) the technical documentation of water pumps;
(b) free access websites of manufacturers of water pumps.
The information shall be provided in the order as presented in points (1) to (15). The information referred to in points (1) and (3) to (6) shall be durably marked on or near the rating plate of the water pump.
(1) Minimum efficiency index: MEI ≥ [x,xx];
(2) Standard text: ‘The benchmark for most efficient water pumps is MEI ≥ 0,70’, or, alternatively, the indication ‘Benchmark MEI ≥ 0,70’;
(3) Year of manufacture;
(4) Manufacturer’s name or trade mark, commercial registration number and place of manufacture;
(5) Product’s type and size identificator;
(6) Hydraulic pump efficiency (%) with trimmed impeller [xx,x], or, alternatively, the indication [–.-];
(7) Pump performance curves for the pump, including efficiency characteristics;
(8) Standard text: ‘The efficiency of a pump with a trimmed impeller is usually lower than that of a pump with the full impeller diameter. The trimming of the impeller will adapt the pump to a fixed duty point, leading to reduced energy consumption. The minimum efficiency index (MEI) is based on the full impeller diameter.’;
(9) Standard text: ‘The operation of this water pump with variable duty points may be more efficient and economic when controlled, for example, by the use of a variable speed drive that matches the pump duty to the system’;
(10) Information relevant for disassembly, recycling or disposal at end-of-life;
(11) Standard text for water pumps designed only for pumping clean water at temperatures below – 10 °C: ‘Designed for use below – 10 °C only’;
(12) Standard text for water pumps designed only for pumping clean water at temperatures above 120 °C: ‘Designed for use above 120 °C only’;
(13) For pumps designed specifically for pumping clean water at temperatures below – 10 °C or above 120 °C, manufacturer must describe the relevant technical parameters and characteristics used;
(14) Standard text: ‘information on benchmark efficiency is available at [www.xxxxxxxxx.xxx]’;

(15) Benchmark efficiency graph for MEI = 0,7 for the pump based on the model shown in the Figure. Similar efficiency graph shall be provided for MEI = 0,4.

Figure Example of a benchmark efficiency graph for ESOB 2900
Further information may be added and may be complemented by graphs, figures or symbols.

ANNEX III Measurements and calculations
For the purposes of compliance and verification of compliance with the requirements of this Regulation, measurements and calculations shall be made using designated standards, or using other reliable, accurate and reproducible methods, which take into account the generally recognised state of the art, and produce results deemed to be of low uncertainty. They shall fulfil all of the following technical parameters.
The hydraulic pump efficiency, as defined in Annex I, is measured at the head and flow corresponding to the best efficiency point (BEP), part load (PL) and over load (OL) for full impeller diameter with clean cold water.
The formula for calculating the required minimum efficiency at best efficiency point (BEP) is as follows:
ηΒΕΡmin requ=88,59 x + 13,46 y−11,48 x2−0,85 y2−0,38 x y−CPump Type,rpm
Where,
x = ln (ns); y = ln (Q) and ln = natural logarithm and Q = flow in [m3/h]; ns = specific speed in [min–1]; C = value found in Table.
The value of C depends on the pump type and nominal speed, and also the MEI value.

Table
Minimum efficiency index (MEI) and its corresponding C-value depending on the pump type and speed
C-value for MEICPumpType,rpm	MEI = 0,10	MEI = 0,40
C (ESOB, 1 450)	132,58	128,07
C (ESOB, 2 900)	135,6	130,27
C (ESCC, 1 450)	132,74	128,46
C (ESCC, 2 900)	135,93	130,77
C (ESCCi, 1 450)	136,67	132,3
C (ESCCi, 2 900)	139,45	133,69
C (MS-V, 2 900)	138,19	133,95
C (MSS, 2 900)	134,31	128,79
The requirements for part load (PL) and over load (OL) conditions are set at slightly lower values than those for 100 % flow (ηΒΕΡ).
ηPLmin, requ= 0,947 ×ηBEPmin, requ
ηOLmin, requ= 0,985 ×ηBEPmin, requ
All efficiencies are based on full (untrimmed) impeller. Vertical multistage water pumps are to be tested with a 3 stage (i = 3) version. Submersible multistage water pumps are to be tested with a 9 stage (i = 9) version. If this number of stages is not offered within the specific product range the next higher number of stages within the product range is to be chosen for testing.
Words in Annex 3 substituted (31.12.2020) by The Ecodesign for Energy-Related Products and Energy Information (Amendment) (EU Exit) Regulations 2019 (S.I. 2019/539), reg. 1(3), Sch. 2 para. 14(7); 2020 c. 1, Sch. 5 para. 1(1)

ANNEX IV Product compliance verification by market surveillance authorities
The verification tolerances defined in this Annex relate only to the verification of the measured parameters by Great Britain authorities and shall not be used by the manufacturer or importer as an allowed tolerance to establish the values in the technical documentation or in interpreting these values with a view to achieving compliance or to communicate better performance by any means.
When verifying the compliance of a product model with the requirements laid down in this Regulation, for the requirements referred to in this Annex the authorities of Great Britain must apply the following procedure—
(1) The Great Britain authorities shall verify one single unit of the model.
(2) The model shall be considered to comply with the applicable requirements if:
(a) the values given in the technical documentation pursuant to paragraph 1(2) of Part 1 of Schedule 1A to the Ecodesign for Energy-Related Products Regulations 2010, and, where applicable, the values used to calculate these values, are not more favourable for the manufacturer or importer than the results of the corresponding measurements carried out pursuant to paragraph 1(2)(b)(vii) of Part 1 of Schedule 1A to those Regulations; and
Words in Annex 4 para. (2)(a) substituted (31.12.2020) by The Ecodesign for Energy-Related Products and Energy Information (Amendment) (EU Exit) Regulations 2019 (S.I. 2019/539), reg. 1(3), Sch. 2 para. 14(8)(c)(i); 2020 c. 1, Sch. 5 para. 1(1)
Words in Annex 4 para. (2)(a) substituted (31.12.2020) by The Ecodesign for Energy-Related Products and Energy Information (Amendment) (EU Exit) Regulations 2019 (S.I. 2019/539), reg. 1(3), Sch. 2 para. 14(8)(c)(ii); 2020 c. 1, Sch. 5 para. 1(1)
(b) the declared values meet any requirements laid down in this Regulation, and any required product information published by the manufacturer or importer does not contain values that are more favourable for the manufacturer or importer than the declared values; and
(c) when the Great Britain authorities test the unit of the model, the determined values (the values of the relevant parameters as measured in testing and the values calculated from these measurements) comply with the respective verification tolerances given in Table 2.
(3) If the results referred to in point 2(a) or (b) are not achieved, the model shall be considered not to comply with this Regulation.
(4) If the result referred to in point 2(c) is not achieved, the Great Britain authorities shall select three additional units of the same model for testing.
(5) The model shall be considered to comply with the applicable requirements if, for these three units, the arithmetical mean of the determined values complies with the respective verification tolerances given in Table 2.
(6) If the result referred to in point 5 is not achieved, the model shall be considered not to comply with this Regulation.
(7) ...
Annex 4 para. (7) omitted (31.12.2020) by virtue of The Ecodesign for Energy-Related Products and Energy Information (Amendment) (EU Exit) Regulations 2019 (S.I. 2019/539), reg. 1(3), Sch. 2 para. 14(8)(d); 2020 c. 1, Sch. 5 para. 1(1)
The Great Britain authorities shall use the measurement and calculation methods set out in Annex III.
The Great Britain authorities shall only apply the verification tolerances that are set out in Table 2 and shall only use the procedure described in points 1 to 6 for the requirements referred to in this Annex. No other tolerances, such as those set out in designated standards or in any other measurement method, shall be applied.

Table 2
Verification tolerances
Parameters	Verification tolerances
Efficiency at BEP (η ΒΕΡ )	The determined value shall not be lower than the declared value by more than 5 %.
Efficiency at PL (η ΡL )	The determined value shall not be lower than the declared value by more than 5 %.
Efficiency at OL (η ΟL )	The determined value shall not be lower than the declared value by more than 5 %.
Substituted by Commission Regulation (EU) 2016/2282 of 30 November 2016 amending Regulations (EC) No 1275/2008, (EC) No 107/2009, (EC) No 278/2009, (EC) No 640/2009, (EC) No 641/2009, (EC) No 642/2009, (EC) No 643/2009, (EU) No 1015/2010, (EU) No 1016/2010, (EU) No 327/2011, (EU) No 206/2012, (EU) No 547/2012, (EU) No 932/2012, (EU) No 617/2013, (EU) No 666/2013, (EU) No 813/2013, (EU) No 814/2013, (EU) No 66/2014, (EU) No 548/2014, (EU) No 1253/2014, (EU) 2015/1095, (EU) 2015/1185, (EU) 2015/1188, (EU) 2015/1189 and (EU) 2016/2281 with regard to the use of tolerances in verification procedures (Text with EEA relevance).
Words in Annex 4 substituted (31.12.2020) by The Ecodesign for Energy-Related Products and Energy Information (Amendment) (EU Exit) Regulations 2019 (S.I. 2019/539), reg. 1(3), Sch. 2 para. 14(8)(a) (as amended by S.I. 2020/1528, regs. 1(2), 6(1)(2)(b)(xiii)); 2020 c. 1, Sch. 5 para. 1(1)
Words in Annex 4 substituted (31.12.2020) by The Ecodesign for Energy-Related Products and Energy Information (Amendment) (EU Exit) Regulations 2019 (S.I. 2019/539), reg. 1(3), Sch. 2 para. 14(8)(b) (as amended by S.I. 2020/1528, regs. 1(2), 6(3)(4)(b)(xiii)); 2020 c. 1, Sch. 5 para. 1(1)
Word in Annex 4 substituted (31.12.2020) by The Ecodesign for Energy-Related Products and Energy Information (Amendment) (EU Exit) Regulations 2019 (S.I. 2019/539), reg. 1(3), Sch. 2 para. 14(8)(e)(i); 2020 c. 1, Sch. 5 para. 1(1)
Word in Annex 4 substituted (31.12.2020) by The Ecodesign for Energy-Related Products and Energy Information (Amendment) (EU Exit) Regulations 2019 (S.I. 2019/539), reg. 1(3), Sch. 2 para. 14(8)(e)(ii); 2020 c. 1, Sch. 5 para. 1(1)

ANNEX V Indicative benchmarks referred to in Article 6
At the time of entry into force of this Regulation, the indicative benchmark for the best available technology on the market for water pumps is a minimum efficiency index (MEI) ≥ 0,70.