- Latest available (Revised)
- Original (As made)
This is the original version (as it was originally made). This item of legislation is currently only available in its original format.
1.—(1) A local authority must undertake check monitoring in accordance with this Part.
(2) Check monitoring means sampling for each parameter listed in Table 1 in the circumstances listed in that table in order—
(a)to determine whether or not water complies with the concentrations or values in Schedule 1;
(b)to provide information on the organoleptic and microbiological quality of the water; and
(c)to establish the effectiveness of the treatment of the water, including disinfection.
|Aluminium||When used as flocculant or where the water originates from, or is influenced by, surface waters|
|Ammonium||In all supplies|
|Clostridium perfringens (including spores)||Where the water originates from, or is influenced by, surface waters|
|Coliform bacteria||In all supplies|
|Colony counts||In all supplies|
|Colour||In all supplies|
|Conductivity||In all supplies|
|Escherichia coli (E. coli)||In all supplies|
|Hydrogen ion concentration||In all supplies|
|Iron||When used as flocculant or where the water originates from, or is influenced by, surface waters|
|Manganese||Where the water originates from, or is influenced by, surface waters|
|Nitrate||When chloramination is practised|
|Nitrite||When chloramination is practised|
|Odour||In all supplies|
|Pseudomonas aeruginosa||Only in the case of water in bottles or containers|
|Taste||In all supplies|
|Turbidity||In all supplies|
2.—(1) Sampling must be carried out at frequencies specified in Table 2.
|Volume m3/day||Sampling frequency per year|
|> 10 ≤ 100||2|
|> 100 ≤ 1,000||4|
|> 1,000 ≤ 2,000||10|
|> 2,000 ≤ 3,000||13|
|> 3,000 ≤ 4,000||16|
|> 4,000 ≤ 5,000||19|
|> 5,000 ≤ 6,000||22|
|> 6,000 ≤ 7,000||25|
|> 7,000 ≤ 8,000||28|
|> 8,000 ≤ 9,000||31|
|> 9,000 ≤ 10,000||34|
|4 + 3 for each 1,000 m3/day of the total volume (rounding up to the nearest multiple of 1,000 m3/day)|
(2) The local authority may reduce the frequency of sampling for a parameter to a frequency not less than half if—
(a)the local authority is of the opinion that the quality of water in the supply is unlikely to deteriorate;
(b)in the case of hydrogen ion the parameter has had a pH value that is not less than 6.5 and not more than 9.5; and
(c)in all other cases, in each of two successive years the results of samples taken for the purposes of monitoring the parameter in question are constant and significantly lower than the concentrations or values laid down in Schedule 1.
(3) The local authority may set a higher frequency for any parameter if it considers it appropriate taking into account the findings of any risk assessment, and in addition may monitor anything else identified in the risk assessment.
Latest Available (revised):The latest available updated version of the legislation incorporating changes made by subsequent legislation and applied by our editorial team. Changes we have not yet applied to the text, can be found in the ‘Changes to Legislation’ area.
Original (As Enacted or Made):The original version of the legislation as it stood when it was enacted or made. No changes have been applied to the text.
Explanatory Memorandum sets out a brief statement of the purpose of a Statutory Instrument and provides information about its policy objective and policy implications. They aim to make the Statutory Instrument accessible to readers who are not legally qualified accompany any Statutory Instrument or Draft Statutory Instrument laid before Parliament from June 2004 onwards.
Use this menu to access essential accompanying documents and information for this legislation item. Dependent on the legislation item being viewed this may include:
Click 'View More' or select 'More Resources' tab for additional information including: