- Latest available (Revised)
- Original (As made)
This is the original version (as it was originally made). This item of legislation is currently only available in its original format.
23.—(1) A temperature relief valve or combined temperature and pressure relief valve shall be provided on every unvented hot water storage vessel with a capacity greater than 15 litres.
(2) the valve shall–
(a)be located directly on the vessel in an appropriate location, and have a sufficient discharge capacity, to ensure that the temperature of the stored water does not exceed 100°C; and
(b)only discharge water at below its operating temperature when subjected to a pressure of not less than 0.5 bar (50 kPa) in excess of the greater of the following–
(i)the maximum working pressure in the vessel in which it is fitted, or
(ii)the operating pressure of the expansion valve.
(3) In this paragraph “unvented hot water storage vessel” means a hot water storage vessel that does not have a vent pipe to the atmosphere.
Latest Available (revised):The latest available updated version of the legislation incorporating changes made by subsequent legislation and applied by our editorial team. Changes we have not yet applied to the text, can be found in the ‘Changes to Legislation’ area.
Original (As Enacted or Made):The original version of the legislation as it stood when it was enacted or made. No changes have been applied to the text.
Access essential accompanying documents and information for this legislation item from this tab. Dependent on the legislation item being viewed this may include:
Use this menu to access essential accompanying documents and information for this legislation item. Dependent on the legislation item being viewed this may include:
Click 'View More' or select 'More Resources' tab for additional information including: